# Two Wattmeter Method – Balanced Load Condition

The **Two Wattmeter Method** is explained, taking an example of a balanced load. In this, we have to prove that the power measured by the Two Wattmeter i.e. the sum of the two wattmeter readings is equal to root 3 times of the phase voltage and line voltage (√3V_{L}I_{L }Cosϕ) which is the actual power consumed in a 3 phase balanced load.

The connection diagram of a 3 phase balanced load connected as Star Connection is shown below.

**Contents:**

- Determination of Power Factor from Wattmeter Readings
- Determination of Reactive Power by Two Wattmeter Method

The load is considered as an inductive load, and thus, the phasor diagram of the inductive load is drawn below.

The three voltages V_{RN}, V_{YN} and V_{BN}, are displaced by an angle of 120 degrees electrical as shown in the phasor diagram. The phase current lag behind their respective phase voltages by an angle ϕ.

Now, the current flowing through the current coil of the Wattmeter, W_{1} will be given as

Potential difference across the pressure or potential coil of the Wattmeter, W_{1} will be

To obtain the value of V_{YB}, reverse the phasor V_{BN }and add it to the phasor V_{YN} as shown in the phasor diagram above. The phase difference between V_{RB} and I_{R} is (30⁰ – ϕ)

Therefore, the power measured by the Wattmeter, W_{1} is

Current through the current coil of the Wattmeter, W_{2} is given as

Potential difference across the Wattmeter, W_{2} is

The phase difference V_{YB} and I_{Y} is (30⁰ + ϕ).

Therefore, the power measured by the Wattmeter, W_{2} is given by the equation shown below.

Since, the load is in balanced condition, hence,

Therefore, the wattmeter readings will be

Now, the sum of two Wattmeter readings will be given as

The above equation (1) gives the total power absorbed by a 3 phase balanced load.

Thus, the sum of the readings of the two Wattmeters is equal to the power absorbed in a 3 phase balanced load.

Determination of Power Factor from Wattmeter Readings

As we know that,

Now,

Dividing equation (3) by equation (2) we get,

Power factor of the load is given as

### Determination of Reactive Power by Two Wattmeter Method

To get the reactive power, multiply equation (3) by √3.

Therefore, the Reactive Power is given by the equation shown below.

For the Measurement of the Three Phase Power, you can also refer the two topics given below.

**Also See:** Measurement of Three Phase Power: Three Wattmeter Method

**Also See:** Two Wattmeter Method of Power Measurement.

## 5 Comments

excellent

Great explanation

Was really helpful before my exams. Well written!!!

excellent

Thank you, this is an exceptional explanation.